PEI is the leading authority for fuel and fluid handling equipment.
PEI’s Underground Storage Tank (UST) System Inspection and Maintenance Committee met earlier this month and acted on 98 public comments offered to update PEI’s Recommended Practices for the Inspection and Maintenance of UST Systems (PEI/RP900)
Many of the comments were accepted in one form or another. A few suggestions that were not incorporated into RP900 are also of some significance to users of the document.
Here is a summary:
- The scope of the recommended practice was NOT expanded to include UST systems and associated equipment other than that used to store and dispense gasoline, diesel and related petroleum products at vehicle fueling facilities. In other words, the document is not intended to apply to marinas, aviation-fueling facilities, farms, emergency generators, etc. The committee did broaden the scope to include the shear valve.
- The Committee recognized that, in many instances, the new federal inspection requirements that became effective October 13, 2015, were less comprehensive than the inspection practices contained in the 2008 edition of RP900. After reviewing all the inspection requirements of the federal rule, the Committee revised the document to meet or exceed the walkthrough inspection requirements and frequencies contained in the federal regulations. In a few instances, the Committee included recommended procedures for walkthrough inspections in the document that were not included in the federal rule. The Committee also rejected several proposals to increase the frequency of some inspections (e.g., spill bucket drain valves, interstitial space of drain valves).
- A number of comments dealt with water and the quality of fuel in the UST. The Committee made a few tweaks to Section 188.8.131.52 that now requires the owner to check to see if water is present and, if found, to notify the appropriate person in the company. Section 184.108.40.206 also will direct the owner to a new appendix that will discuss water issues and suggest strategies to keep water out of the tank. The appendix will be available for public review and comment before it is included in the 2016 edition of RP900.
- All of the testing requirements contained in RP900 were removed from the document and will be considered for inclusion in PEI’s Recommended Practices for the Testing and Verification of Spill, Overfill, Leak Detection and Secondary Containment Equipment at UST Facilities (PEI/RP1200). By this action, the Committee opted to provide one document to use for walkthrough inspections of UST systems (RP900) and another to test the equipment and verify it is working properly (RP1200). As a result of this decision, both RP900 and RP1200 will be released simultaneously, probably sometime this summer.